Type FTS Fault Throwing Switches
The purpose of the M.L.E. Fault Throwing Switch is to create a deliberate fault on an overhead line, responding from a signal given by the protective relays of a malfunctioning transformer. Tripping of the source circuit breaker which senses the fault will automatically cut off all of the system being supplied. It is, therefore, customary to isolate the faulty transformer quickly, in the ‘dead period’ before the circuit breaker recloses, by means of an M.L.E. type RLS spring opening switch, initiated to open by a late closing auxiliary switch on the FTS.
The switch portion is basically a single pole M.L.E. type RDB disconnector to which has been added a closing spring toggle, which in the closed ‘straight-line’ position locks the switch closed to prevent bounce and throw open by the short-circuit forces encountered on closing. At near ground level is positioned the spring close mechanism in a weatherproof galvanised housing. This also contains two powerful closing springs which in the service position are restrained by a lever released by a trip solenoid. An adjustable length of galvanised pipe couples the mechanism to a clevis on the switch.
The M.L.E. type FTS will make without welding closed on to a 40kA peak, and withstand 20kA for 3 seconds, and is rated up to 72.5kV
Type FTS Fault Throwing Switches (Cat. No. FTS/11) >>
Complete Product Catalogue
To view our latest complete product catalogue, simply click here. You will need a PDF viewer such as Adobe Reader to view the electronic catalogue, which will take a short time to download. If your browser does not already include this you can click here to download Adobe Reader for free.
Quick Specification Form
If you would like a quotation for any of our equipment please download and complete our electronic "Quick Specification Form" (click here to download form), and email it to or
Please provide the maximum possible information at the time of your enquiry. Receipt of the requested information with the enquiry will save time-consuming correspondence, and avoid unnecessary delays in submitting a comprehensive quotation.
If you have any other queries or would like more information about our equipment, please use our Contact Form.